Connector for RPLUS reinforced supports that allows the connection of threaded rods to the ceiling, wall or channel for the configuration of an E90 fire-resistant installation. Mounted by fixing C / DIN 603 M6x20 or hexagonal M8 bolts.
It allows the connection of threaded rods to the range of the reinforced RPLUS supports, both to the ceiling and wall or channel.
Provides greater resistance to installation. Increase the load capacity of the support system.
CE conformity to directive 2014/35 / EU. Fire resistance E90, according to DIN 4102-12.
GC protection system (standard UNE-EN ISO 1461), suitable for outdoor installations and in aggressive environments. Corrosion resistance class 6.
Suitable for the creation of fire-resistant installations with E90 approval according to DIN 4102-12 for Rejiband® and Pemsaband® trays in cable conduction in electrical and telecommunications installations that demand high safety requirements in public buildings, infrastructures and civil works, industrial facilities and tertiary sector.